EV CHARGING TRANSFORMER
Electric Vehicle charging infrastructure must be developed rapidly to keep up with the expected exponential growth of electric vehicles over the next several years.
MGM Transformer, located in California, is at the epicenter of Electric Charging infrastructure development. We work directly with Automobile OEMs and other industry participants to not only design suitable transformers for Level 3 and 4 charging, but also support the overall optimization of the electrical charging system.
- 10KVA to 10MVA
- Product offerings in both dry type and liquid filled to meet your specific demands.
- 220°C Nomex insulation for Dry-Type Transformers
- Self-Cooled or Forced Air Cooled
- Low Voltage or Medium Voltage solutions
Level 1: Uses onboard car charger at 120V | 2-5 miles per hour of charging
Level 2: Uses onboard car charger at 240V or 208V, up to 80A but typically at 30A | 10-11 miles per hour of charging
Level 3: Creates DC from 240V or 480V single or three phase sources | 50-100 miles per hour of charging
Level 4: Creates DC from 240V to 800V single or three phase sources | 170+ miles per hour of charging | 350 kW units can charge for 200 miles in 15 minutes
- High Harmonics: Depending on charger architecture, a charger may present harmonic loadcurrents to the transformer. For chargers that present a significant harmonic load we recommend that a K-factor rated transformer be considered. Depending on the harmonic
spectrum, a K-factor in the range of K=4 to K=9 is usually required.
- Power Quality: National standards put limits on the amount of charger harmonics that maybe transmitted through the transformer to the power line. This harmonic transmission canbe reduced by transformers with multiple, phase shifted, secondary windings; electrostatic shields; and harmonic mitigating, zig-zag, windings.
- Local Environmental Conditions: If a transformer is installed in a non-temperature controlled area, 80°C or 115°C temperature rise units can contend with high ambient temperatures. Enhanced type NEMA 3R enclosures can be used if horizontally blowing rain or snow are a concern
- Safety: Units should be installed in areas that are not accessible to the general public. If that is not possible, additional options can be considered including tamper resistant hardware, hinged and lockable enclosures or non-ventilated enclosures. Local Electrical codes may require bollards or other features to protect transformers from vehicle damage. Transformers also should not be installed near water lines, water drains, etc., which could direct water onto the enclosure if broken
- Low Site Voltage: Use integral taps or buck-boost transformers to adjust the voltage input to the transformer
BULL RUSH PROGRAM
MADE IN USA
MGM Transformer Company can manufacture your units at our 120,000 square foot plant in the U.S. and source the raw materials solely from American companies if required. By doing so we can certify your units to be compliant with any of the various “Buy U.S.” statutes (either state or federal). Please make sure to specify your requirements at the time of order.
INSTRUCTION SHEETS & MANUALS